COMMERCIAL HOT WATER HEATING UP TO 60 DEGREES
Conventional water heaters can account for up to 35% of your total energy bill, and contribute significantly to your carbon footprint. When the time comes to replace your water heater, it makes sense to upgrade to a more efficient and environmentally friendly solution to provide your home or business with fast reliable hot water.
NEXT EVOLUTION IN WATER HEATING
- 60 degrees hot water
- Air operation range from -15°C to 45°C
- Extremely energy efficient
- C.O.P of up to 4.68
- Fast & stable hot water supply
- Ideal for high volume hot water applications
- Suitable for any size commercial application
NEXT EVOLUTION IN COMMERCIAL HOT WATER HEATING
The Evo Rapid is ideal for commercial water heating applications, including apartment complexes, sports and recreation clubs, schools, dormitories and student accommodation.
HOT WATER UP TO 60°C
The Evo Rapid provides hot water up to 60°C
Air operation range
The Evo Rapid will work efficiently in air operating temperatures from -15°C to 45°C
FAST & STABLE HOT WATER
Evo Rapid is designed with an advanced control logic specifically tailored to commercial applications, which commits to fast and stable hot water supply.
OZONE FRIENDLY REFRIGERANT
The Evo Rapid heat pump uses R410A refrigerant which is recognised as the green refrigerant in the industry while delivering a safe and stable running performance.
Maintain a High C.O.P.
The Evo Rapid is capable of maintaining a high C.O.P. of up to 4.68 due to its smart technology including green refrigerants, heat exchanger with innovative technology and circulating heating principle.
|Rated Heating Output||kW||17.2||19.6||32.0||37.0||43.4||88.8|
|Rated Power Input||kW||3.80||4.2||7.20||7.90||9.31||19.2|
|Max. Running Current||A||9.2||10.7||18.0||21.0||22.8||47.0|
|Max. Power Input||kW||5.85||6.8||11.0||12.0||12.9||28.2|
|Hot Water Volume||L/h||370||413||688||795||933||1908|
|Suggested Tank Volume||m3||4||5||8||9||10||20|
|Fan Motor Input||W||120x2||120X2||200X2||200X2||200X2||750X2|
|Water Flow Volume||m3/h||3.0||3.4||5.5||7.5||7.5||15.5|
|Water Pressure Drop||kPa||60.0||90.0||110.0||105.0||108.0||100.0|
|Water Connection||inch||1||1||1-1/4||1-1/2||1-1/2||DN65 Flange|
|Air Discharge Type||/||Horizontal||Horizontal||Vertical||Vertical||Horizontal||Vertical|
|Condenser||/||Patented tube in shell heat exchanger||Patented tube in shell heat exchanger||Patented tube in shell heat exchanger||Patented tube in shell heat exchanger||Patented tube in shell heat exchanger||Patented tube in shell heat exchanger|
|Suggested Water Temp||°C||55||55||55||55||55||55|
|Max. Water Temp||°C||60||60||60||60||60||60|
|Casing||/||Galvanized Metal||Galvanized Metal||Galvanized Metal||Galvanized Metal||Galvanized Metal||Galvanized Metal|
|Net Dimensions (L/W/H)||mm||1050/400/1245||1050/400/1245||1420/750/970||1420/750/970||1557/605/2052||2180/1080/2100|
|Shipping Dimensions (L/W/H)||mm||1100/455/1380||1100/455/1380||1100/455/1380||1500/875/1250||1500/875/1250||2360/1280/2260|
Test conditions: ambient temperature 20°C/15°C, water circulation from 15°C to 55°C. The data above is for reference only. For more specific data, please contact EvoHeat on 1300 859 933
WARRANTY, PARTS & SERVICE
For further peace of mind EvoHeat offer a 2-year warranty on the compressor, 2 years on parts and 1 year on site labour.
EvoHeat have a comprehensive network of specialist service agents nationally to ensure maximum equipment uptime. Spare parts are kept in stock in the extremely unlikely event that they are required.
Evo 270- Nice to have hot showers again. Much more refined than the old heat pump it replaced (different brand). The unit is quiet and easy to use. It has some very good features such as an anode that can be easily replaced from the side of the unit. The installation by KMS was prompt & very neat (better than previous install.) I would highly recommend this unit & the installers.
Evo 270- We decided upon a heat-pump system to help us save on power costs and our installer recommended Evoheat 270. We could not be happier with our choice and that decision. The unit itself looks good and it is very efficient to run. We also noticed a big difference in the water temperature compared to our old one which used to be scalding hot. This is so much better.